The information in this manual is subject to change without notice. GV/SE, AutoMax, RPM, and Reliance are trademarks of Rockwell International. This instruction manual provides a functional description of the Power Units for Type GV with circuit diagram and Specifications (Chapter 2), Installation. Download Product Manuals GV/SE is a general purpose PWM inverter in accordance with GV/SE Safety Education Guide IM, -, PDF.
|Published (Last):||19 October 2013|
|PDF File Size:||20.71 Mb|
|ePub File Size:||15.34 Mb|
|Price:||Free* [*Free Regsitration Required]|
Move the jumper to the desired setting as shown in figure 2. Reconnect the motor to the drive. Be sure to verify that parameters P.
The signal is available through the terminal strip. Regulator Board Description List of Tables Table 2. Identification of the protective conductor Warning signs and item identification If a fault occurs, the drive will coast-to-rest stop and a 2- gv30000 3-digit fault code will flash on the display.
UL Class J, V, time delay, or equivalent. When total lead length exceeds 76 meters feetnuisance trips can occur caused by capacitive current flow to ground. Continue g3v000 section C. Table of Contents Add to my manuals Add.
Note that no devices are to be mounted mmanual the drive. Refer to figures 2. Chapter 9 Troubleshooting The Drive Page 51 – Figure 4. No additional filter installation is required. Page 38 – Table 3. Mounting The Drive On HP drives, close the outer cabinet door.
Contains a communication access door that allows access to the communication port without removing the cover. Page 84 – Figure 9. Be sure there is adequate clearance for air circulation around the drive. Conduit Entry Opening Sizes Refer to figures 4. On — HP drives, close the inner and outer cabinet doors. Page 50 – Figure 4. Refer to section 5.
Page 58 – Installing Gv300 Wiring from an External The encoder connects to terminals 4 through 9 of the Regulator board terminal strip as shown in table 7. Page 24 – Figure 2. Page 82 Appendix D. HAPTER Completing the Installation This chapter provides instructions on how to perform a final check of the installation before power is applied to the drive.
Reliance Electric GV Manuals
Note that depending on hv3000 setting of parameter P. The required mounting hardware is supplied with the filter. This manual also for: Component is defective if: Intended for general-purpose indoor applications. When adding more than one grounding conductor wire to a single chassis ground, twist the conductors together.
Download Product Manuals | Reliance Electric Limited
Stopping Gvv3000 Drive Failure to observe this precaution could result in bodily injury. To reduce line disturbances and noise, motor lead length should not exceed 76 meters feet for any non-Reliance Electric motor or any non-inverter duty motor.
Setting The Analog Output Jumper j17 Page Identification of the protective conductor Warning signs and item identification EN Section Title Protection against electrical shock 6. Note that HP drives may be supplied with an optional AC disconnect. List of Figures Figure 2. Page of Go.
Reliance Electric GV3000 Instructions Manual
Chapter 5 Installing Input Power Wiring Wiring Requirements For The Drive Operator Interface Module Connector Mznual 35 – Figure 3. Wire the DC input power leads by routing them according to drive type. Page 55 Page 56 – Figure 5.